* CAM is not included with this model number. The valves with the CAM are model number 4402, 4403, and 4404.
The 4000 line of indexing valves offers a reliable, economical way to automate multiple zoned residential and small commercial irrigation systems.
These patented indexing valves allow for the number of watering zones to be changed quickly and easily. They are ideally suited for both city water and pump applications and may also be used for onsite wastewater or effluent water applications. The simplicity of design and few moving parts ensures ease of maintenance and long service life.
The 4000 valve is available in 4 or 6 outlet models. A quick change of the cam allows the valve to operate with flows as low as 10 GPM and at pressures of 25 to 75 PSI.
- High Impact ABS Polymer Construction-High Strength, non corrosive body for long product life.
- Available in 4 and 6 Outlet Models-Can quickly and easily change from two to six watering zones.
- Simplicity of Design-Valves are easily maintained and serviced for long product life.
- Operates at Low 10GPM and Pressures of 25-75 PSI-Reliably automates multiple zoned residential and small commercial irrigation or wastewater systems.
- Two year limited warranty.
- Flow Rate: 10 - 25
- Inlet: 1 1/4" x 1"
- Inlet Thread: Slip
- Pressure Rating: 25 - 75 PSI
- We Recommend the Installation of an Atmospheric Vacuum Breaker
Between the Pump and the Valve.
1. PROBLEM: Valve Does Not Change or Cycle to Next Zone or Outlet.
- CAUSE: The stem and disk assembly is not rotating when the water flow is turned OFF and then back ON.
- SOLUTION: Ensure there is no debris inside the cam. Clean and carefully reinstall the cam.
- SOLUTION: If fewer than the maximum number of outlets are being used, check the installation of the cam. Ensure that the stem and disk assembly is not being held down by an improperly installed cam. Refer to the Cam Replacement Instructions.
- SOLUTION: Remove the valve top and check for proper movement of stem and disk assembly. Check for and remove any debris or foreign objects that may jam or retard the movement of the disk.
- SOLUTION: Check for freedom of movement of stem and disk assembly up and down over the center pin in bottom of valve. Scale deposits may build up on the pin and hold stem and disk assembly down. Clean pin and again check for freedom of movement.
- SOLUTION: Be sure that all operating outlets are not capped and that the flow to operating zones is not restricted in any manner. This would cause pressure to build up in the valve and lock the stem and disk assembly in the down position.
SOLUTION: The back flow of water from uphill lines may be preventing the valve from cycling properly. This can happen when the valve is placed too far
below an elevated irrigation line. If the valve cannot be placed close to the
high point of the system, a check valve should be installed near the valve in
the outlet line that runs uphill from the valve.
2. PROBLEM: Water Comes Out of all the Valve Outlets
- CAUSE: Stem and disk assembly not seating properly on valve outlet.
- SOLUTION: Check for sufficient water flow. A minimum of 10 GPM is required to properly seat the disk. For water flow between 6 and 10 GPM, a stem and disk assembly with a lighter spring is available.
- SOLUTION: Remove the valve top and check the inside walls to ensure that nothing is interfering with the up and down movement of the stem and disk assembly inside the valve.
- CAUSE: Too many sprinkler heads on a zone will cause insufficient pressure for disk to seat over valve outlet.
- SOLUTION: Reduce the number of heads on the zone to obtain the proper sprinkler operating pressure.
- CAUSE: For a pump installation, the pump may be losing its prime, causing the water flow to surge. This will cause the valve to cycle quickly several times, skipping one or more zones. Verify that the flow to the valve is constant by removing the valve top and watch the flow when the pump is turned ON after having been OFF for at least 15 minutes. The flow should be steady and uninterrupted.
- SOLUTION: Seal any pump suction line leaks.
- SOLUTION: Replace or install suction line check valve to prevent pump from losing its prime.
- CAUSE: The stem and disk assembly is being advanced past the desired outlet.
- SOLUTION: Ensure that the correct cam for the desired number of zones is installed and that the outlet lines are installed to the correct outlet ports of the valves as indicated by the zone numbers on the top of the cam.